How to add a 4Way Switch
How to Add a 4Way Switch with Other Light Switches: I need help adding a 4-way switch in my home.
Wiring a 4Way Light Switch with 3Way Switches
Electrical Question: I need help adding a 4-way switch in my home.
- I’m looking for help and diagram for adding a 4-way switch in my home.
- I have some experience with basic wiring but 3-way and 4-way switches can be confusing.
- The additional switch will be used for my basement light circuit.
- I want to add a switch at the bottom of the basement steps.
- The Current setup with two 3-way switches
- Switch #1
- Is located at the top of the steps.
- The power source feeds into this switch box.
- The feed to the lights is from the switch box.
- Switch #2
- Far side of basement.
- Just a switch fed from switch #1.
- Switch #1
This home electrical wiring question came from Gary, in Rumney, New Hampshire.
Thanks for your electric wiring question Gary.
Adding a 4Way Switch to Two 3Way Switches
Application: Wiring a 4-Way Light Switch.
Skill Level: Intermediate to Advanced – Best installed by a Licensed Electrician.
Tools Required: Basic Electricians Pouch Hand Tools and Power Tools for installing electrical wiring, and Voltage Tester.
Estimated Time: Depends on personal level experience and ability to work with hand and power tools.
Precaution: Identify the lighting circuit, turn it OFF and Tag it with a Note before working with the wiring.
Notice: Installing additional 3-way or 4-way switch wiring should be done according to local
and national electrical codes with a permit and be inspected.
Wiring a 4-Way Switch in with two 3-Way Switches
In some areas of the home we may need more than two light switches, especially in long hallways with multiple entryways. This is an example where one or more 4-way switches may be installed.
- In this application where two 3way switches already exist, a 4way switch may be added by simply installing two 2-wire with ground cables of the same wire gauge as the circuit wiring from either of the 3way light switches to the location of the new 4way switch.
- A 4way switch has two marked sets of screw terminals where the two wires of each 2-wire cable will attach.
- The 2-wire cables intercept the two traveler wires at the 3way switch location which are located at one end of the 3way switch.
- The two 2-wire cables are basically creating a loop of the pair of traveler wires through the 4way switch.
- Marking or identifying the white wires of the 2-wire cables as black or red is required to indicate that the wires are being used for switching, and be sure to ground the light switch.
Diagrams and Instructions for Wiring a 4-Way Light Switch
- Fully explained 4 way switch diagrams. 4-way switches are a convenient way to operate lighting fixtures from three or more locations.
The electrical wiring adds additional wiring to the same principles of 3-way switching.
3 Way Switch Wiring Diagrams
- 3 Way Switch Wiring Diagrams Fully Explained.
- Detailed Electrical Wiring Diagrams and Pictures assist your Home Electrical Projects.
Basement Electrical Wiring
- Fully Explained Photos and Wiring Diagrams for Basement Electrical Wiring with Code Requirements for most new or remodel projects.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about 4 Way Switch Wiring, Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Wiring Basement Light Fixtures||Welder Circuit 230 Volt|