Heat Pump Problems and Electrical Power
How to Troubleshoot Heat Pump Problems: My heat pump isn’t working right, is there a problem with the home electrical service or local utility transformer and the heat pump circuit breaker?
Heat Pump Electric Circuit
Electrical Question: My heat pump isn’t working right, is there a problem with the home electrical service or local utility transformer and the heat pump circuit breaker?
- Is it an electrician’s responsibility to make sure the service to the home can handle a new device they install?
- An electrician was hired to install a heat pump which replaced an oil furnace.
- The heat pump never functioned properly as it was under powered which caused hard starts, etc.
- Now the new heat pump isn’t functioning properly and it has been determined that the home electrical service and the local utility transformer to the breaker box couldn’t meet the amperage requirements of the heat pump.
- Was it the installing electrician’s responsibility to make sure the service was proper?
This electrical question came from: Edward, from Grants Pass, Oregon.
Thanks for your electrical repair question Edward.
How to Troubleshoot Heat Pump Problems
Application: Heat Pump Problem and Evaluating a Home Electric Service Panel.
Skill Level: Advanced – Best performed by a Licensed Electrical Contractor.
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Tester and amp meter or load recorder.
Estimated Time: Depends on the type and age of the electric service panel and the access to the circuits to be evaluated.
Precaution: This is a project that should be performed by a Licensed Electrical Contractor and typically requires specifications in accordance with the local utility company or electric service provider.
Notice: Making changes to the Home Electrical Service Panel should be done according to local and national electrical codes with a permit and be inspected.
The Heat Pump Electric Power Source
- Heat Pump Circuit
The circuit for the heat pump must be sized according to the exact heat pump unit that is being installed and by consulting the electrical circuit requirements described in the Installation or Owners Manual.
- The Main Electrical Service
The electrical panel of the home must have enough available amperage and capacity for the proposed heat pump circuit. For best results an electrical contractor may be hired to install the heat pump circuit.
- The Electrical Utility Provider
Often the electric utility company may refer to large 240 volt electrical loads at the home in order to accurately size the transformer which supplies power to a new home, and typically the electrician does not have information about the utility company transformer size.
- Installing a New Heat Pump
When the homeowner decides to install large equipment such as a new heat pump which will add a substantial load to their electrical service it would be good to contact the local utility company and inform them so they may check the size of the service equipment and decide if any adjustments will be required.
- Main Electrical Service Capacity
The installing electrical contractor should make sure that the home electric service panel has the extra capacity for the additional load of the heat pump. Typically the size of the service transformer is not known by the electrical contractor because the local utility company owns the transformer and they alone have access to the equipment.
More about Heat Pumps and Electrical Circuits
Heat Pump Wiring
Heat pumps are used for heating and cooling. Wall mounted units are great for offices, sun rooms, room additions, garages and are used in hotel and motel rooms.
House Wiring Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electrical Panel Circuit Listing
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring, Heat Pump Repair and Home Electrical Wiring:|
|« Previous||Next »|
|Sizing an Electrical Circuit for a Motor Home||Is Your Electric Clothes Dryer Shocking You?|