Generator ATS Provides Power During Partial Power Loss
How a Generator Automatic Transfer Switch Works and is a Very Important Part of the Home Generator System
A Generator HTS/ATS Can Provide Power When One Leg Of Power Is Lost
[ad#block]Question: I am in a building in Summit county where there are no known power outages. I am assuming there is three phase coming in to our building by the looks of the transformer outside. We have a backup generator which is a Generac Elite series that is supposed to supply backup power for half of the building. Earlier today the power went out in 1/3 of the building.
- I am assuming just one phase went out, and so the generator kicked on and has been supplying power ever since. Now the reason I am thinking just one phase went out is because we have two HTS transfer switches.
- One has standby operation lit with utility power not lit, and the other has utility power lit and the switch position is utility. Is it possible that there is a problem with the power company that just one of the phases are down? And if so, should I report this as a power outrage?
Background: Eric, a Other from Stow Ohio
Thanks for your electrical question Eric.
How a Automatic Generator Transfer Switch Works
- Eric, I don’t believe this is a problem with the utility company because the power failure has affected only one third of the building.
- I would check the main circuits upstream from the functioning HTS/ATS where you may find that you have a tripped breaker or lost one leg of the three phase power, therefore the ATS is doing it’s job by automatically providing generator power due to a electrical circuit failure.
This series covers a wide variety of topics all about home generators including sizing, selecting, connecting and safely operating this all important addition to your home.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Automatic Transfer Switch, Generator and Home Electrical Wiring:|
|« Previous||Next »|
|How Bad Advice Can Burn Your House Down||How To Safely Remove A Broken Light Bulb|