GE Breaker Type Prevents Dryer From Working – Part 1
How to Fix a GE Breaker Problem: Dryer Circuit Requires Corrected 220 Volt Circuit, I recently attempted to install a new dryer using 240V – 4wire installation procedures.
Dryer Circuit Requires Corrected 220 Volt Circuit
Electrical Question: I recently attempted to install a new GE DSXHS47 front load Dryer using 240V – 4wire installation procedures.
Although unit manual shows it is 3-wire single phase, I believe I am able to utilize the 4 wire installation as well and simply remove the white neutral grounding and replacing it with the cords 4-wire green ground wire, then rerouting the neutral white back onto itself.
The Problem with The Dryer
- Dryer works as I have both Red and Black hot leads at 120V each leg, and the Dryer spins, but am not receiving any “TEMPERATURE” lights off of the dryer and the dryer is not producing any heat period.
- The book’s troubleshooting indicates a blown leg of a breaker so I went ahead and replaced the already brand new 30-Amp Breaker with an all new 40-Amp breaker. I have put both the red and black leads in the breaker, placed the white neutral lead to the panel’s other white leads, but using a totally unused screw point. Then put the bare ground wire also on the panel into it’s own grounding screw point.
- The 4-wire plug has also been wired correctly I believe as I followed the installation procedures for black, red, white and ground to this receptacle, so I must have something wrong “I BELIEVE” within the neutral wiring of the dryer itself.
- I need to know where I went wrong. The drum spins, but no LED on the Dryer panel and no heat, but yet the multi meter shows 120V each red and black lead from panel to inside of Dryer.
- I get a 120V reading touching red meter lead to both red and black leads and black meter lead to ground point, however I get “nothing” when attempting to meter test touching red meter lead to both red and black leads and black meter lead to neutral.
This tells me I believe I have something not configured correctly within the neutral itself.
I believe I just need to know a bit more about neutral wiring as it relates to power sources?
Please review and advise!
This electrical wiring question came from: Gary a Homeowner from Calif.
Thanks for your electrical wiring question Gary.
How to Fix a GE Breaker Problem
240 Volt Dryer Circuit
- All electric dryers require a dedicated 30 amp, 240 volt circuit.
- When properly installed the receptacle at the dryer location will produce these readings
- 120 volts from each Line to Ground
- 240 volts Line to Line, consisting of the 2-pole circuit.
- Electrical circuit testing should be done with the cover installed.
- 240 volt circuits should be installed with a permit and inspected.
The Following will assist you with your Dryer Circuit
House Wiring Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electrical Wiring Protection using Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Wiring a Dryer
Wiring a Dryer
See an electric dryer installation with a typical 220 Volt electric power cord wiring system. You may find yourself with either a 3-wire or 4-wire electric dryer, or a 3-wire or 4-wire outlet. Lets look a how the electric dryer is wired and what to do if your cord does not match the plug.
Troubleshooting Electrical Wiring Problems
Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical and Home Electrical Wiring:|
|« Previous||Next »|
|Making Pigtails for Ground Wire Connections||Nicked Electrical Outlet Wiring and Greasy Stuff|