Electrical Wiring for Closet Light Fixtures
How to Install Closet Lighting – This method of lighting for a closet is fine because the fluorescent light fixture provides an area that is approved for making the wiring connections and bonding the ground wire to the frame of the light fixture.
Electrical Wiring Methods for Closet Lighting
[ad#block]I have 2 small closets in my house that each have a single fluorescent bulb fixture above the inside of the door affixed to the header.
- There is no box, simply a Romex wire coming through the wall (sheet rock).
- I want to change this. I know the header will prevent me from installing a box.
- I haven’t been able to find any fixtures that will work with the current setup. What do you suggest?
This electrical wiring question came from: George, a Homeowner from Lawrenceburg, Tennessee.
Additional Comments: Great.
Thanks for your electrical wiring question George.
How to Install Closet Lighting
- This method of lighting for a closet is fine because the fluorescent light fixture provides an area that is approved for making the wiring connections and bonding the ground wire to the frame of the light fixture.
- Basically the light fixture has a junction box enclosure installed within the light fixture.
- The wiring methods for protecting and splicing the wiring are to be followed when using this type of light fixture.
Home Electrical Wiring Codes
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Fluorescent, Lighting and Home Electrical Wiring:|
|« Previous||Next »|
|Outside Lighting Wiring Diagram||Wiring Diagrams for Wiring Lights from a Wall Plug|
I have 2 kitchen light fixtures that are currently working off one switch. I would like them to work independently on seperate switches. My contractor tells me it can’t be done because it’s Romex and there is no conduit. I don’t know what kind of Romex it is wired with. I just want to know if my contractor is right or if he is just giving me the run around.
From my experience you hit the nail on the head, you just got the run around. Now granted, I can’t see exactly how your home is built and if there is access to get to the wiring, but basically where there is a will, there is a way with just about anything. Mary, if you have an attic above your kitchen, then it may just be a matter of fishing a wire down the wall and making a few changes with the wiring to separate the switches.
It would be interesting to note that your contractor is not keeping track of the current improved devices that can be installed to provide wireless or automation control capabilities which work just like the remote controls for ceiling fans and their light fixtures. These devices are available from your local hardware store.
The funny thing is that these devices have been available for years, however most people just never heard about them!
Thanks Dave –
There is a bedroom above the fixtures in the kitchen so the Romex is not accessible. Is there no way just to split the Romex at the switch? Or would a new wire have to be run?
I’m not sure how the automation devices work. I have a ceiling fixture and a pendant light that are running off the same switch. Is it possible to add one of these devices to a ceiling fixture?
Here are a few more options for controlling these two lights separately:
In order to control one of the lights with a separate switch additional wiring would be required. This could be accomplished by installing surface mounted wire mold (which looks nicer than ordinary round conduit).
Another way is to use automation devices as previously mentioned. The controlling devices connect to the existing 120 volt wiring which enable the devices to transmit and receive signals to perform control operations, such as turning light fixtures on or off. The switches serve as transmitters, and control modules at the fixture locations serve as receivers. These devices are easily set up to provide switch control functions. The only requirement is that there is a 120 volt power source at each location.
Keep in mind that the control switches can be installed anywhere there is 120 volts, in fact controllers are available where you can plug into a wall outlet and have the same switching control functions.