» Need Electrical Help? Get a Quick Reply! Ask the Electrician
Electrical Wiring for a Garage Workshop
Installing an Electric Panel for a Detached Garage: Electric Codes for a Detached Garage Panel, Can I use a Main Lug Only Electric Panel Load Center for a detached garage?By: Dave Rongey
Garage and Workshop Electrical Wiring
Electrical Question: Can I use a Main Lug Only Electric Panel Load Center for a detached garage?
- I intend to electrify a detached garage, which is about 60 ft. from the house panel.
- The Power needs will be convenience outlets and lights for a workshop.
- The project and circuits to be installed are the following:
- I will use two 30Amp circuits, 3 wire + equipment ground, #10 wire, in 3/4″ underground PVC conduit to provide the power to the garage.
- I plan to install a 30Amp load center in the garage with two 20Amp circuit breakers.
- Can I use an MLO or Main Lug Only Load Center or do I need a Main Disconnect as well?
This electrical question came from: Jim, a Property Manager from Urbana, Illinois.
Thanks for your electrical question Jim.
Installing an Electric Panel for a Detached Garage
Application: Installing an Electric Panel for a Garage or Workshop.
Skill Level: Advanced – Best installed by a Certified Electrician or Licensed Electrical Contractor.
Tools Required: Electricians pouch of hand tools and the various power tools necessary for the specific method of electrical service installation.
Estimated Time: Depends on the type of panel, the location, and available access to the project area.
Precaution: This is an extensive project. Working in an electric panel has shock and arc flash hazards and should be performed by a Certified Electrician or Licensed Electrical Contractor.
Notice: Installing an Electrical Panel should be done according to local and national electrical codes with a permit and be inspected.
Electric Codes for a Detached Garage Panel
Jim, because the garage is detached it would be best to have a main disconnect, however please see the following electrical codes that will apply to your question.
- The panel may not have more than 6 circuit breakers.
- If the number of circuit breakers are more than 6 then a main disconnect is required.
- NEC Electrical Code Reference articles 225.31, 225.32, 225.33, 225.36.
More about Wiring a Garage or Workshop
Home Electrical Codes
- Electrical Code Directory covering electrical boxes, electrical circuit, electrical code outlets, electrical grounding, electrical services, electrical underground, and electrical wiring methods.
- Garage Electrical Wiring
- Garage electrical wiring diagram and considerations for wiring garage circuits, complete with pictures.
- Careful planning for your garage with immediate and future equipment considerations will help you understand how to size your electrical circuit requirements.
- This information will help as an garage electrical wiring guide.
- House Wiring Circuits and Circuit Breakers
- This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
- Electric Circuit Listing
- The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
- Electrical Wiring Protection using Circuit Breakers
- A guide to home electrical circuit breakers and how they work to protect your electrical wiring.
- When properly installed, your home electrical wiring is protected by a circuit protection device.
- Electrical Wire for the Home
- Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring, Garage Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Does Electricity Travel Through the Air?||How to Install Wiring for a Ceiling Light Fixture|