» Need Electrical Help? Ask the Electrician
Electrical Question about Electrical Code for Main Service Wires
Can I pull a load circuit (2wires) through the same conduit as the incoming main service wires?
Electrical Question from Tim about Electrical Code
Received from Tim a Electrician
[ad#block]Question: Can I pull a load circuit (2wires) through the same conduit as the incoming main service wires
example- I need to run a conduit on the outside of the house; the only way to get to the breaker box is to run the conduit to the overhead meter socket then run the wires through the conduit running from the meter socket to the breaker panel in the house with the service wires from the meter socket to the breaker panel
Thanks for your electrical question.
Hi Tim – NEC Article 230-7 states that the Feeder and Branch circuit conductors are not permitted in the same conduit or raceway with the service conductors.
The Following links will assist you with your electrical question:
For more information about Electrical Code
This link is helpful as a Electrician
Electrical Code Articles
Make sure not to miss these Resources for: Wiring Diagrams
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
The following may also be helpful for you:
Electrical Wiring Video #2
Home Electrical Wiring Videos about this Topic and More
Dave's Companion Guide to Home Electrical Wiring:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|More articles about Electrical, Industrial and Home Electrical Wiring:|
|« Previous||Next »|
|Electrical Question about A Kettle Plug That Gets Very Hot||Can I use Aluminum Wire for the RV Electrical Service?|