Electrical Code and Protecting NM Cable
Installing and Protecting NM Electrical Cable – The NM Cable must be positioned and fastened so that the cable will be protected from damage especially when the wall coverings are installed.
Providing Protection for Electrical NM Cable
Electrical Code Question: In a wood framed wall with studs positioned so the wall cavity is 1-1/2″ deep.
How is a vertical length of NM cable supported on the edge of the stud.
The CJ appears to protect only the length of the cable within the support.
Is the balance of the cable protected by its flexibility to move out of the way?
This electrical code question came from: Jim, a Educator from Florissant, Missouri
Thanks for your Electrical Code Question Jim.
Installing and Protecting NM Electrical Cable
- The NM Cable must be positioned and fastened so that the cable will be protected from damage especially when the wall coverings are installed.
- The NM Cable must be secured to protect it from sheet rock screws to avoid penetrating the NM cable.
- If the depth of the wall does not provide enough depth and safety space then installing the electrical wiring using metal conduit or armored cable may be necessary.
- Check with your local building inspector who has been assigned to your project for a determination.
The Following will assist you with your Electrical Code Question:
For more information about Electrical Code
Home Electrical Code
Electrical Code Directory covering AFCI circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, electrical GFCI, electrical-grounding, electrical-project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-codes and smoke-detectors.
This link is helpful as a Educator
Home Electrical Projects
The following may also be helpful for you:
Electrical Wiring Video #2
Home Electrical Wiring Videos about this Topic and More
Learn more with my Home Electrical Video Course:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|More articles about Electrical Code NEC and Home Electrical Wiring:|
|« Previous||Next »|
|Why Kitchen Outlets Stop Working||Is Your 240 Volt Outlet Safe|