Electrical Power Circuit For An RV
How do I go about connecting wire to the service panel and also to the RV? Electrical Circuit Power Requirements for an RV Circuit. RV units have either a 30 amp or 50 amp electrical hookup connection.
Planning The Power Requirements for an RV Circuit
[ad#block]Electrical Question: How do I go about connecting wire to the service panel and also to the RV?
- I am trying to connect my 1995 Coachmen RV, located at a remote hunting camp, to a 100 amp service box that is approximately 120 ft. from the RV.
- I need approximately 30 amps to power the A/C + water pump, lights, microwave, and etc.
- I have read that in order to carry 30 amps over 120feet I would need to utilize #6 AWG copper wire.
- My question is how do I go about connecting this heavy wire to the service panel and also to the RV?
- The RV currently has a 3-prong cord that is used to connect to a power source outlet.
This electrical wiring question came from: Tom, a Homeowner from Eatonton, Georgia.
Additional Comments: I am very thankful that there is someone like you to help with electrical questions as electrician resources in my area are extremely limited.
Thanks for your electrical wiring question Tom.
Electrical Circuit Power Requirements for an RV
- 30 amp 125Volt RV Cord
A 30 amp 125Volt RV cord is typically #10 Copper Wire, 3 wires total. One hot, one neutral, one ground.
- 50 amp 240Volt RV Cord
A 50 amp 240Volt RV cord is typically #6 Copper Wire, 4 wires total. Two hots, one neutral, one ground.
- RV Pedestal Outlet
The typical power connection at the RV location should be a 30 or 50 amp RV pedestal outlet.
- 30 amp 125Volt RV Cord
Increasing the Length of a RV Cord, Making an RV Cord Longer
- Due to the distance involved, the dedicated circuit should should be designed after making a complete listing of the electrical loads that will be connected and the required electrical power for all of these electrical devices that will be used in the RV.
- Once the total connected load for all of these devices has been determined the wire size may be calculated based upon the length of the cord.
Increasing the Electrical Service to an RV
- Keep in mind that the RV electrical capacity is limited to the amperage of the main breaker in the RV panel. Sizing the cable properly prevents voltage drop, it does not increase the amperage.
- The limitation of the RV power is always based upon the size of the electrical panel in the RV Even if an adapter is used to connect a 30amp cord to a 50 amp RV outlet source the RV is still limited to 30 amps.
- NOTE: The original question explains the limitation: “The RV currently has a 3-prong cord that is used to connect to a power source outlet.” The original electrical service is the limitation.
- IMPORTANT: The main circuit breaker cannot be up-sized (or exchanged with a larger circuit breaker), doing so would cause a potential fire hazard. The whole electrical panel service wiring and cord must be properly sized and upgraded in order to expand to a larger amperage.
More about RV Cord and Electrical Wiring for an RV
House Wiring Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
For more information about RV Wiring
RV Electrical Wiring Topics
Electrician Answers Questions about mobile home electrical circuit, rv main breaker trips and wiring rv outlets.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring, RV and Home Electrical Wiring:|
|« Previous||Next »|
|4 Way Switch Wiring Diagrams||Installing Two 3 Way Dimmer Switches|