Does My Sauna Require A Dedicated Electrical Circuit?
The sauna will require a dedicated 240 volt 40 amp GFCI Protected Circuit installed according to…
Electrical Question from Mike about Wiring a New Sauna
Background: Mike, a Homeowner from Ontario Canada
[ad#block]Question: I am installing a sauna in my basement. I was hoping to use a power cable that ran to an old water heater – 30 amp breaker 2 wire 10 gauge. However the sauna heater is rated at 7.5kW and the voltage is 240 V. The heater unit is marked 31.2 amp. Can I use the existing cable or do I have to run #8 with a 40 amp breaker. The current cable runs behind a wall and would be a pain to replace.
Thanks for your electrical question Mike. The sauna will require a dedicated 240 volt 40 amp GFCI Protected Circuit installed according to applicable electrical codes. Take your time, but do it right. What a great opportunity to do something different! Besides, just think how great it’s going to feel soaking away and knowing you did it right!
The Following links will assist you with your electrical question:
For more information about Home Wiring
Home Wiring Diagrams
This link is helpful as a Homeowner
Make sure not to miss these Resources for: How-To-Videos
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
The following may also be helpful for you:
Electrical Wiring Video #2
Home Electrical Wiring Videos about this Topic and More
Learn more with my Home Electrical Video Course:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|More articles about Electrical, GFI-GFCI, Sauna Tub and Home Electrical Wiring:|
|« Previous||Next »|
|How To Troubleshoot 3-Way Switch Wiring||How To Provide GFCI Protection For An Older Kitchen?|