Question – Dimmer Switches – Part 2
When lights that are on dimmer switches don’t work, make sure you understand the difference between Master and Slave dimmer switches.
Last problem we discussed was solved. New problem, I installed two track lights and two ceiling fans in the place of recessed lights. The ceiling fan motors have their own circuit, but the lights on the fans are on the same circuit as the track lights, which are on three-way dimmer switches (here we go again).
These are 600-watt switches. After combining the wattage of each bulb on this circuit, totals to 880 watts. – POOF!
I only removed the old lights and installed the new lights and they do not work, the lights that is! Please help!!!
I checked both switches, one switch has power going into the switch and power from the switch.
[ad#block]I think this is because the dimmer is fried. You can test it by shutting off the power and installing a standard 3-way switch in place of the dimmer. Mark your wires so you know what goes where. Usually the two wires paired close on the dimmer are the travelers and the one by itself is the “Point” which is the power or the line going to the fixtures, depending on how your 3-ways are wired.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Dimmer Switch Questions and Home Electrical Wiring:|
|« Previous||Next »|
|Question – Dimmer Switches – Part 1||Electrical Problems after a Lightning Storm with Circuit Breaker|