Causes of Lost Power to Pool Equipment
What would cause the loss of power to my pool equipment? I have a built-in pool that has two motors, the circuit breaker tripped and the lights in one of my bathrooms dimmed.
Testing and Identifying a Pool Equipment Circuit Problem
Electrical Question: What would cause the loss of power to my pool equipment?
- I have a built-in pool that has two motors, one for the in-pool cleaning system, and one for the filter. The power to these two motors is each routed through a 15 amp double-pole circuit breaker on a circuit board by the pool equipment.
- Power to this circuit board is run through a dedicated 30-amp double pole breaker on my main house circuit board. This morning I found the 30-amp breaker had tripped, but neither of the two 15 amp breakers for the two pool motors. I reset the 30-amp and turned on the pool pump motor. About 20 minutes later the 30-amp breaker tripped again.
- Now it sounds like I might have an issue in the wiring between my main board and the pool board, but that is not my question. A strange thing happened when the 30-amp breaker tripped the second time.
- The lights in one of my bathrooms dimmed to about half, as well as the lights in the adjoining bedroom. Slowly, lights and appliances in other parts of the house, on different breakers, began to dim and eventually just went dead (a cascading effect).
- I ran to the main circuit board and noticed that the little wheel on the main meter was turning very, very slowly. I first tried to reset the 30-amp pool breaker, that did nothing. I then reset the main 200-amp breaker. The first time had no effect. I turned off the main breaker and waited about two minutes, then flipped it back on and everything came back to life, and has been working ok for the rest of the day so far knock on wood.
- I however have left the 30-amp pool breaker off. My question is, what on earth would cause this cascading loss of power from a single breaker being tripped? Do I have a bigger problem than either a faulty breaker or faulty power lines for the pool?
I look forward to your response.
This electrical question came from: Dave, a Handyman from Tempe, Arizona
Thanks for your electrical question Dave
Loss of Electrical Circuit Power to Pool Equipment
Application: Troubleshooting Circuit Power to Pool Equipment.
Skill Level: Advanced. This electrical wiring project is best performed by a Licensed Electrical Contractor or Certified Electrician.
Tools Required: Basic Electricians Pouch Hand Tools, Voltage Tester or Volt Ohm Meter.
Estimated Time: Depends on the type and age of the electrical wiring and the access to the circuits and wiring to be evaluated.
Precaution: This is a project that should be performed by a Licensed Electrical Contractor and typically requires specific tests of the electrical circuits.
Notice: Repairs to Home Electrical Wiring should be done according to local and national electrical codes and installing new or replacement electrical parts or equipment may require a permit and inspections.
- Dave, to determine the cause of this problem all of the pool equipment should be turned off or disconnected so that the 30 amp circuit can be tested. If the 30 amp circuit does not trip off then there is a problem with the pool equipment. If the 30 amp circuit trips off again then I would suspect that there is a problem with the 30 amp circuit leading from the electrical panel to the pool equipment.
- All of the circuit wiring and connections will require testing to identify the fault and then the necessary repairs will be required. The problem may be due to a direct buried cable that has a direct short to ground , or it may be due to a problem with a connection at one of the electrical enclosures. This is best tested and repaired by a qualified licensed electrician who will make the necessary repairs and then test the required GFCI protection as needed for the pool equipment.
More about Electrical Wiring and Circuit Breakers
Electrical Circuit Wiring
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Understanding Digital Volt Meters
When working on home electrical wiring using voltage meter can play an important part in electrical safety. Electrical testers and voltage meters enable you to identify electrical circuits and help prevent the possibility of accidental electrical shock.
Types of Electrical Testers
Using Electrical Testers and Voltage Meters
For more information about Lost Power
Why Your Home Lost Power
How to Identify Lost Power
Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Pool Equipment and Home Electrical Wiring:|
|« Previous||Next »|
|Causes of Lost Power to Receptacle Circuit||Kilowatts and Kilowatt hours KWH|