Causes of Incorrect Electrical Voltage
Why is the Voltage wrong at the Electric Service Panel? How to Troubleshoot Incorrect Voltage Readings.
Troubleshooting Incorrect Voltage Problems
Electrical Question: Why is the voltage wrong at the electric service panel?
This is a residential service in a mobile home park, 120/240 volt, grounded, however this could also happen at any residential or home electrical panel.
- Line1 to Neutral and Ground = 113 volts.
- Line2 to Neutral and Ground = 137 volts.
- Line1 to Line2 = 009 volts, not a typo.
- Neutral to Ground = 337 volts, not a typo.
- What do I have happening here?
- I have been a licensed electrician for 40 years and never run into this.
This electrical troubleshooting question came from: Roy, a Contractor from Payson, Arizona.
Thanks for your electrical troubleshooting question Roy.
How to Troubleshoot Incorrect Voltage Readings
Skill Level: Advanced – a Licensed Electrical Contractor should be consulted.
Tools Required: Basic Electricians Pouch Hand Tools, Ammeter and Voltage Tester.
Estimated Time: Depends on age of the home, the condition of the electrical system and available access to electrical components.
Precaution: Electrical troubleshooting of this level is best performed by a qualified electrical contractor.
The Causes of Incorrect Voltage Readings at an Electrical Service Panel
- Roy – you have two possibilities that is causing these voltage readings:
- One of the main incoming lines has a loose or burnt connection (my guess is L2 because L1 to N reading is correct) or you have an Open Neutral, which could be a loose or burnt connection as well.
- Roy, your getting a voltage feed-back due to one line that has been lost.
- Also, keep in mind that in Mobile Home Parks they have a 4-wire system, where the ground and the neutral are Isolated and this will explain why the high reading on the neutral to the ground, which is again due to the loss of one of the incoming main lines.
- Thoroughly inspect the main panel, especially the incoming service wires.
Check the cables at the main lugs and at any main breakers.
Don’t rule out that a connection of a breaker to the panel buss may be bad due to corrosion or arcing.
- If the problem is not found at the the home panel location then go upstream to where the power source. Many mobile home parks are fed from a large main distribution panel at another location. Be careful and keep yourself well insulated. The voltage on the neutral can be lethal as you know.
Continued Discussion, Electrician to Electrician, Roy’s Reply:
Hi Dave, Thanks for the reply,
I have been a licensed electrician since 1967 and never run into this before. I have had back feeds for one reason or another but not to this extent. The open has to be upstream because this condition exists at the power pedestal meter. I am surprised that none of the neighbors have complained about a similar problem. I had forgotten or never realized the mobile home parks were a true 4 wire system, thanks for that info. I will let you know what we find as soon as I get somewhere with this problem.
Dave’s Follow Up:
Thanks Roy, Yes, these feed backs can be a little interesting to say the least.
There is a possibility that other homes may be affected, it just depends on where the problem is. If the entire service checks out OK and the whole main panel has the same voltage readings then the problem may be with the utility company. Every once and a while one of their transformers may go bad and can produce a feedback like this too. I have seen this happen at the meter socket as well. Be Careful.
Dave’s Note: Problems like this require a Professional Licensed Electrical Contractor.
The Following will assist you with Electrical Troubleshooting
You identified your project to be about Troubleshooting, so you might find this information useful:
Troubleshooting Electrical Wiring
Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Troubleshooting, Volt Readings and Home Electrical Wiring:|
|« Previous||Next »|
|What To Do With Incorrect Electrical Wiring||Bathroom Heater Electrical Wiring|