Can I Wire my Dryer to my Range Outlet?
Can I use my range outlet for my dryer? Why Wiring a Clothes Dryer to a Range Outlet is Unsafe.
Wiring a Clothes Dryer Circuit
Electrical Question: Can I use my range outlet for my dryer?
Peter in Vermont asks:
- My question is pretty simple Dave. I have an old house with a 50amp range receptacle that the stove is plugged into. I want to put a clothes dryer right next to the stove (without running a separate drop).
- Can I simply split that range drop in a large jbox, mount the range receptacle in that jbox, and continue out of that jbox upstream to a 30 amp breaker in an enclosure, then terminate at a 30amp dryer receptacle?
- The idea here is that the 30amp breaker for the dryer is ahead of the 50amp breaker for the range, therefore it should trip if the dryer draws over current beyond 30a.
- Obviously in this scenario you may not be able to run the range and dryer at the same time (depending on how many elements you are running simultaneously on the range) without tripping the 50a breaker in the panel.
Please tell me your thoughts on this. Thanks.
Thanks for your electrical wiring question Peter.
Add to the Wiring a Clothes Dryer
Application: Wiring a Clothes Dryer Circuit.
Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrical Contractor, or Certified Electrician.
Electrical Tools Required: Basic Electricians Pouch Hand Tools, Voltage Tester, and appropriate Safety Gear.
Estimated Time: Depends on the personal level experience, ability to work with tools, install electrical circuit wiring, and the available access to the project area.
Electrical Safety: Identify the electrical power source to the Clothes Dryer, turn it OFF and Tag with a Note before working with the electrical wiring.
Electrical Wiring Parts and Materials: Electrical parts and materials for the Clothes Dryer should be approved for the specific project and compliant with local and national electrical codes.
Electrical Codes and Inspections: Installing or changing home electrical wiring should be done according to local and national electrical codes as adopted in your specific area of Vermont. A permit and inspections may also be required.
Why Wiring a Clothes Dryer to a Range Outlet is Unsafe
This electrical wiring project is about Wiring a Clothes Dryer in an older house.
A Clothes Dryer Requires a Dedicated Circuit
- Peter, from the information you have provided, (and I get this question a lot), the answer is simply this: The NEC Code requires a dedicated circuit to each large appliance.
- Here are some examples:
A dryer requires a 4 wire 30 amp dedicated circuit (NEC article 250.142(B).
An electric range 8.75 kW or higher requires a minimum 40 amp dedicated circuit (NEC article 210.19(A)(3).
- The same is true for any permanently installed large appliance or equipment.
- The NFPA – National Fire Prevention Association
These are Fire and Safety Regulations and Codes that have been carefully developed and adopted to prevent hazardous conditions for you and your home, and to ensure that the appliances and equipment that will be used will be protected and function with dependability.
- Note: I believe thee are all concerns that you have as well, and for good reason, and it would be wrong for me to advise you in any other way.
- Appliance and Equipment Specifications
Every UL Approved electrical appliance that is to be used or installed provides the required electrical circuit specification which is typically found in the installation manual which comes with the appliance.
More about Electrical Wiring for a Clothes Dryer
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Electrical Junction Boxes for Home Wiring
Understanding electrical junction boxes and what they are used for. Home electrical wiring is the process of installing electrical wire to a location that will serve electrical devices or an appliance. One very important component is the box where the wire will be installed. The type and size of the home wiring electrical boxes will depend upon the circuit size, application and its location.
Kitchen Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Kitchen Electrical Wiring with Code Requirements for most new or remodel projects.
Wiring a Kitchen Range Power Cord
Fully Described Electric Range Installation with a typical 220 Volt electric power cord wiring system. You may find yourself with either a 3-wire or 4-wire electric range. Lets look at how the electric range is wired and what to do if your cord does not match the plug.
Laundry Room Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Laundry Room Electrical Wiring with Code Requirements for most new or remodel projects.
3-Wire and 4-Wire Configurations for Clothes Dryers
See an electric dryer installation with a typical 220 Volt electric power cord wiring system. You may find yourself with either a 3-wire or 4-wire electric dryer, or a 3-wire or 4-wire outlet. Lets look a how the electric dryer is wired and what to do if your cord does not match the plug.
Electrical Code Articles for Home Wiring
Electrical Code Directory covering AFCI circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, electrical GFCI, electrical-grounding, electrical-project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-code, and smoke-detectors.
Home Wiring Projects
Installing electrical wiring projects for safety and home improvements
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Code NEC, Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Wire a Generator Transfer Switch Video||Upgrading Electrical Wiring for Home Buyer Safety|