» Need Electrical Help? Ask the Electrician
Can I Replace a 15amp for a 20amp Breaker?
When I have the lights on and use anything it pops the breaker. Can I change the 15amp to a 20amp breaker?
15amp Circuit Breaker Problem
Electrical Question: When I have the lights on and use anything it pops the breaker. Can I change the 15amp to a 20amp breaker?
Tripping Breaker Main Panel
I have a big garage, the entire garage is on the same 15 amp circut. When I have the lights on and use anything else it pops breaker. example air compressor or 120v welder, fans. not all at the same time but I was wondering if I can replace the 15 amp for a 20amp breaker. house was built in 2018.
This electrical wiring question came from Charles in Surprise, Arizona.
Thanks for your electrical wiring question Charles.
Tripping 15amp Breaker Problem
Application: Tripping Breaker a Main Panel.
Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrical Contractor, or Certified Electrician.
Electrical Tools Required: Basic Electricians Pouch Hand Tools, Voltage Tester, and appropriate Safety Gear.
Estimated Time: Depends on the personal level experience, ability to work with tools, install electrical circuit wiring, and the available access to the project area.
Electrical Safety: Identify the electrical power source to the Main Panel, turn it OFF and Tag with a Note before working with the electrical wiring.
Electrical Wiring Parts and Materials: Electrical parts and materials for the Main Panel should be approved for the specific project and compliant with local and national electrical codes.
Electrical Codes and Inspections: Installing or changing home electrical wiring should be done according to local and national electrical codes as adopted in your specific area of Arizona. A permit and inspections may also be required.
Tripping Breaker a Main Panel in a Attached Garage
This electrical wiring project is about Tripping Breaker a Main Panel in the Attached Garage of a New Home.
Overloaded Circuit Causes a 15amp Breaker to Trip Off
- Charles, from the information you have provided, No – the 15amp circuit cannot be replaced with a 20amp circuit breaker because this would cause the electrical wiring to overheat which could create a potential fire hazard.
- It would be best to have an additional electrical circuit installed in the garage.
See More about Tripping Breaker a Main Panel
Sub-Panel Electrical Wiring for the Home
Electrical sub-panel wiring considerations for the home complete with pictures. Careful planning for your Sub-Panel with immediate and future load considerations will help you understand how to size your Sub-Panel. This information will help as you consider a Sub-Panel and its size.
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Garage Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Garage Electrical Wiring with Code Requirements for most new or remodel projects.
Work Shop Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Workshop Electrical Wiring with Code Requirements for most new or remodel projects.
The following may also be helpful for you:
Electrical Wiring Video #2
Home Electrical Wiring Videos about this Topic and More
Dave's Companion Guide to Home Electrical Wiring:
|More articles about Electrical Repair and Home Electrical Wiring:|
|« Previous||Next »|
|Replace a Light Switch with a Motion Detector Switch||Wiring a Shed with Outlets and a Light|
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.