Air Conditioning Circuit Breaker Trips Off
Why does my air conditioner keep tripping the circuit breaker? Problem with a air conditioning unit.
Problem with an Air Conditioning Circuit Breaker
[ad#block]Air Conditioning Question: Why does my air conditioner keep tripping the circuit breaker?
My central Air Conditioning unit was not cutting off even when the temp was reached. The compressor would shut off but not the unit in the basement, even when I switched it off at the thermostat. So I manually switched off the power switch on unit. I left it off for about 40 minutes, when I switched it back on, the unit came on, but now it keep tripping the breaker after about 20 seconds. I don’t know if burner on the furnace is trying to re-start and won’t so that whats tripping it. Can I lock out the burner, start the furnace again a run the air conditioning without the burner until I can get a service tech out?
Its an Oneida-Royal Furnace.
Background: WGM, a Homeowner from Connecticut.
Thanks for your electrical question WGM.
Central Air Conditioner
A Central Air Conditioning unit has several components, including:
The control thermostat, the motor and air circulation unit, the compressor unit and condenser coil fan.
Air Conditioner Tripping the Breaker
Typically, a tripping circuit breaker is caused by a problem with the compressor unit. The main problems are due to a condition within the compressor unit. This can include the compressor unit icing up, which may be caused by a dirty or blocked condenser coil unit, or a fault with the condenser fan, which could be a bad motor, or a bad motor capacitor. There are many variables and factors which are best identified by a qualified air conditioning service technician.
Safety First: Do not defeat any safety or limit switches.
It does sound like a limit switch has failed or a component in the control circuit. I would advise calling a qualified air conditioning technician to identify and repair the problem. In the mean time to avoid damage to the unit I would not run the unit if it is tripping the circuit breaker off.
The Following will assist you with your electrical question:
For more information about Circuit Breaker
This link is helpful as a Homeowner
Make sure not to miss these Resources for: How-To-Videos
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Air Conditioner, Electric and Home Electrical Wiring:|
|« Previous||Next »|
|220 Volt Hot Tub Circuit Wiring||Troubleshooting Half Power At The Electrical Panel|
Hello how are you?
I am writing you today to ask you a question about my air conditioner.
I had a new air conditioner unit put in about 6 years ago. I live in FL and do not use the AC Heat that often, but everytime I put the heat on after about 3 min the circuit breaker trips. I put the circuit breaker back on a the ac heat starts working again and then the ac circuit breaker trips again.
I went into the circuit breaker box and took out the breaker for the AC and noticed one of the wires looks a little burnt.
My question today is if you can give me some reason(s) as to why this was happening, and a way to fix this problem.
Thanks – Garfield