Air Conditioner and Tripping Circuit
My Air Conditioner trips the circuit breaker, does the breaker need to be replaced? Troubleshooting an Air Conditioner Problem.
Problem with Air Conditioner Circuit
[ad#block] Electrical Question: My Air Conditioner trips the circuit breaker,does the breaker need to be replaced?
- I live in a 60 year old co-op condo with a dedicated 220 volt line for a new 22,000 BTU in wall air conditioner.
- There is an outlet with a 20amp breaker wired to it approx 18 inches off the floor.
- A new single 220 volt outlet was tapped off the outlet from the floor and put underneath the a/c which is approx 5 feet off the floor.
- The breaker trips occasionally. The voltage ranges around 210 volts and 12.2 amps taking a reading from the outlet near the floor.
- Only the AC is on this line, and I’ve tried plugging the a/c in the top and bottom outlet at different times, and the breaker trips with both.
- There is #12 wire was used to feed the new (top) outlet. Is it as simple as a bad breaker?
I appreciate any help in this manner. Thanks, Rob.
This electrical question came from: Rob, from Whitestone, New York.
Thanks for your electrical question Rob.
Air Conditioner Tripping Circuit Breaker
Application: Replacing a 220 Volt Circuit Breaker for an Air Conditioner.
Skill Level: Advanced – Best performed by an Electrical Contractor or a Licensed Electrician.
Tools Required: Electricians pouch of hand tools, voltage tester and protective safety gear.
Estimated Time: Depends on the make and model of the panel and the condition of the existing electrical circuit breakers and wiring methods.
Precaution: For safety the main circuit breaker should be turned off or any other disconnect means that would deenergize the panel before replacing a circuit breaker, however turning off the main circuit breaker may not deenergize all of the areas of the panel components and wiring. This is an extensive project that requires experience and should be performed by a Licensed Electrical Contractor.
Troubleshooting a 20 Amp 220Volt Air Conditioner Problem
Rob, if the original outlet is still in place is there a possibility that it is being used as well by another device? If so this may be contributing to the problem and it would be best if the original outlet was removed, then splice the circuit through and install a blank cover. If the 12.2 amp reading is correct then there may be a Circuit Breaker bad circuit breaker, however the air conditioner may be loading up and creating an overloaded condition as well. If the amperage load shows 12.2 at the time when the circuit Circuit Breaker Problem breaker trips off then the circuit breaker will need to be replaced.
See more about Air Conditioner Circuits and Circuit Breakers
Wiring Electrical Outlets for the Home
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how to wire electrical outlets.
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about 220 Volt Wiring, Electrical and Home Electrical Wiring:|
|« Previous||Next »|
|Electrical Wall Switch Variations||How to Correct 3-Way Switch Wiring|