Wiring Hallway Lights and Switches
By Dave Rongey - Summary:|
How to Wire and Control Light Fixtures in a Long Hallway: Circuit Amperage for Long Hallways and Several Light Fixtures, Wiring Switches for Hallway Light Fixtures, Installing Switches or Occupancy Sensors, Setting the Occupancy Sensor Time Delay,
If this is your first visit, be sure to sign up for your Free Electrical Tips and eBook.
Your Comments and Electrical Questions are always welcome.
Methods for Wiring Hallway Lights and Switches
- There is a door at each end of the hallway and a light and light switch by each door.
- Another light and light switches every 100 feet for a total of 6 lights and 6 switches.
- I can use three of four switches (single pole single throw, double pole single throw, three-way, and four-way).
- I need to wire these switches and lights in a way that only two lights are on at one time. line enters on the right end of the hallway, and this is the entrance door.
- The exit door is on the left end of the hallway.
- This hallway is wired on a single 15 amp circuit.
This electrical wiring question came from: Kevin, a Student from Sunset Hills, Missouri.
See more about Home Wiring for Missouri
Thanks for your electrical wiring question Kevin.
How to Wire and Control Light Fixtures in a Long Hallway
Wiring Switches for Hallway Light Fixtures
- Installing Switches or Occupancy Sensors
- When controlling lighting in a long hallway consider this:Wire the hallway lighting so that each set of two lights is controlled by one occupancy sensor that has a 180 degree sensing range for each light and occupancy sensor zone of the hallway.Each occupancy sensor should be installed in the center of the hallway, or as required due to distances and specs.
- Setting the Occupancy Sensor Time Delay
- Set the time delay setting for each occupancy sensor for the time it will take to walk through each zone, then to be safe double that amount of time.
- Circuit Amperage for Long Hallways and Several Light Fixtures
- Depending on the actual type of lighting that will be used, you may want to consider increasing the circuit to 20 amps and use #12 gauge wire which will help reduce the amount of voltage drop due to the length of the hallway.
- Energy Savings for Hallway Lighting
- This will save energy and provide passage way lighting.As always, check with your local codes as they relate to your location and the type of building application this project is proposed.
More about Electrical Wiring for Hallway Lighting
Wiring a Light Switch – Diagram 1
- Fully Explained Light Switch Wiring Diagrams. Detailed Electrical Wiring Diagrams and Pictures assist your Home Electrical Projects.
- Electrical Wire for the Home
- Guide to Home Electrical Wire
Electrical Wire for the Home
- Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
- Lighting For The Home
- Lighting Electrical Codes
3 Way Switch Diagram
- In response to the requests for this information, I have developed a comprehensive,step-by-step guide designed to walk you through the identification and wiring of your 3-way switches.
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.