Why Space Heaters Can Cause Electrical Outlet Problems
What has caused several outlets to stop working? How to Identify Potential Outlet Wiring Problems where Space Heaters are Used, Fix Electric Outlet Problems Caused by Portable Space Heaters.
Electric Outlets Not Working
Electrical Question#1: What has caused several outlets to stop working?
My brothers 1920’s vintage colonial home has several outlets that are not working. I checked the circuit breakers and none are tripped. I’m getting a reading on my tester of 40-50 volts and 120 between the metal box and the hot side of the receptacle. He says the problem occurred after he left a space heater on overnight. He also has no power in his garage which he says is an older problem.
This electrical troubleshooting question came from: Bob, a Contractor from Agawam, Massachusetts.
Additional Comments: GREAT!
Electrical Question#2: I had a breaker trip which was obviously caused by trying to use 2 space heaters on the same circuit.
- I unplugged one heater before resetting the breaker. Upon the first reset attempt, I heard some buzzing, heard the snap of an obvious arc possibly emanating from my home office area. Of course, immediately after that, the breaker tripped. My wife, sitting at her desk in the office reported a spark and smoke coming from an outlet that is not even included in the circuit with causing problems. Knowing exactly what locations the problem breaker services, I was interested in locating the outlet the buzzing was coming from, so I tried the second reset which buzzed a bit at the breaker box but reconnected. Prematurely claiming victory I realized only one outlet on the problem circuit was working. To make it worse, it’s location is almost exactly “the middle”. One incident occurred that made less sense than the sparking outlet of a separate circuit I mentioned earlier. Upon replacing a known worn switch to the garbage disposal just two locations downstream of “the middle” working outlet I thoroughly checked and rechecked for any voltage getting through to the switch wires which there was none. Since the working outlet serviced the refrigerator and the connections I was working on tested dead, I left the circuit breaker on. In the middle of replacing the switch, of course; the hot touched the ground and scared at least a year off my and my cat Mofus’s lives. It tripped the breaker, i reset it and not one time since has it tested anything but dead. Should I just move?
This electrical wiring question came from Billy, a Handyman in Ochelata, Oklahoma.
Portable Electric Heaters and Outlet Problems
Thanks for your electric wiring question Bob and Billy.
How to Fix Electric Outlet Problems Caused by Portable Space Heaters
- Space Heaters and Electrical Consumption
- Many electric space heaters are a high consumers of electricity and can cause problems with electrical circuits, especially if the electrical wiring is out dated or under sized.
- Space Heater Receptacle Outlet Problem
- The outlet where the electric space heater was plugged into is most likely where the problem is.
- Burnt Plug or Cord
- It is common to find a burnt neutral connection and damage to the electrical outlet.
- Check the Outlet Electric Wire Connections
- I strongly recommend having a qualified electrical contractor make the necessary repairs to the electrical wiring.
- The electric wiring should be inspected for burnt connections and deteriorating receptacle outlets
- Damaged wiring should be repaired or replaced as needed, and the receptacle outlets should be replaced.
- Electrical wiring in older homes should be examined and upgraded and brought up to the current electric codes whenever possible.
- Space Heaters and Smoke Detectors
- For an extra measure of safety, make sure to install and test smoke detectors and GFI outlets where required in older homes.
- PLEASE NOTE:
- Space Heaters can help to save on your electrical bill when they are used correctly and used according to the manufacturers instruction manual.
- Many space heaters require a dedicated circuit which should be installed by a qualified electrical contractor.
- PLEASE NOTE:
Learn More about Home Electric Wiring
- Wiring Electrical Outlet for the Home
- Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
- Electric Circuit Listing
- The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
- Electrical Safety and Voltage Testers
- When working on home electrical wiring, quality voltage testers can play an important part in electrical safety. Electrical testers enable you to identify electrical circuits and help prevent the possibility of accidental electrical shock.
For more information about Electrical Wiring
- Electrical Wiring
- Home electrical wiring projects with pictures and wiring diagrams.
- This link is helpful as a Contractor
Electrical Code Articles
Browse other questions about this topic:
Electrical Outlets Stopped Working Space Heater Problems 40-50 volts, burnt outlet, electric outlets not working, electric wiring, electrical wiring, how to electrical, older home, outlets not working, portable electric heater, portable heater, several outlets, space heaters, wall outlet problem
Or Ask Dave a Question
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.