The Shocking Truth About Neutral Wires
By Dave Rongey - Summary:|
Why There May be Voltage on a Neutral Wire: Some of the worst shocks I have ever received while working on live circuits was from neutral wires, here is why and How You Can Prevent Electrical Shock from a Neutral Wire.
Why Do I Have 120 Volts on a Neutral Wire?
- Is it normal to have 120 volts from a neutral wire?
This electrical wiring question came from: Dan, a Homeowner from Kailua, Hawaii.
Thanks for your electrical wiring question Dan.
Wow – This is a Loaded Question, so here goes!
Why There May be Voltage on a Neutral Wire
- 120 Volts on a Neutral Wire
NOTE: Even though this question lacks a lot of information, (such as what are you testing and how you are testing it), however I will explain a few situations where you are sure to get a 120 volt reading on a neutral wire. Lets say you have an incandescent light bulb in a fixture.
- Light Bulb Circuit Example
The light bulb itself has a small coil of wire which glows bright when power is applied. One side of this coil of wire connects to a hot wire, the other side connects to the neutral wire. When power is applied it runs through the coil, lights it up, and the power flows to the neutral and back to the bonded ground system of the electrical panel. This completes the circuit.
- Disconnected Neutral Wire
Now I disconnect the neutral wire anywhere after the connection to the light bulb, and using a voltage tester connect one lead to the disconnected neutral wire from the light fixture and the other tester lead to the neutral wire that continues to the electrical panel. If the power was turned on to the light bulb the light bulb would not light up, however I will get a 120 volt reading on my tester because the tester has been placed in the middle of the neutral wire which runs back to the electrical panel and my tester is in fact completing the circuit in a very limited way due to the internal circuitry of the type of tester being used.
- The Flow of Electricity
The amount of electricity flowing through the tester depends on the type of tester being used. If the tester is a digital type then no current would flow through the tester, but if the tester was an inductive type that has a coil of wire then there will be a flow of electrical current that goes through the tester, yet in each instance the amount of electricity would depend on the resistance of the tested circuitry.
Now for the Shocking Truth about Neutral Wires
- Shocks from a Neutral Wire
If you understand the explanation above then you should realize just how easy it is to get an electrical shock from a neutral wire, in fact some of the worst shocks I have ever received while working on live circuits was from neutral wires. This happens when the circuit is completed either by the connection of the neutral wire path back to the ground system or any other connection that is grounded including a person.
- Resistance and the Circuit Path
The shock can be lethal because of the amount of electricity that can flow through the person due to the connected load and their resistance or lack of resistance a person may have to a ground source. The danger takes place if a person gets into the awkward position of being right in the middle of the neutral path to ground, and it hurts like the dickens, can knock you on your rear end, throw you across the room, cause you to yell, or any manner of uncomfortable results including possible lethal results including death!
- Turn Off the Circuit
This is why it is extremely important to always positively identify and turn off any electrical circuit that you may be working on, even if you are working on just the the neutral wires, because if you become grounded or caught in the middle, your sure to get shocked, and this is called Not Fun!
More about Home Electricity
Using electrical testers
Electrical Safety and Voltage Testers
When working on home electrical wiring, quality voltage testers can play an important part in electrical safety. Electrical testers enable you to identify electrical circuits and help prevent the possibility of accidental electrical shock.
Troubleshooting Electrical Wiring
Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
Learn How to Wire it Right!
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.