Switch Wiring for a Bath Exhaust Fan
By Dave Rongey - Summary:
How to Wire a Single Switch for a Bathroom Exhaust Fan: Understanding Switch Wiring for a Bathroom Exhaust Fan.
Exhaust Fan Switch
- I just removed a recessed light from above my shower. It had three sets of wires connected. One coming from breaker, one to switch and I am not sure where the other goes. The wires were all live when I had them apart.
- I put in a Light and Vent Exhaust Fan Combo. I couldn’t fit all the wires back in so I tried a junction.
- I connected the original three wires to a new wire. I then ran the new wire to the fan. It was working until I turned off the switch in the bathroom. It sparked and threw the breaker.
- Now the Breaker trips every time I try to reset it. Do I possibly have too much connected?
- All I added was the new wire so that I didn’t have to connect them all to the vent fan like they were with the recessed light. The home was built in 1985.
This electrical wiring question came from: James, a Homeowner from California.
Additional Comments: Very Helpful
Thanks for your Electrical Wiring Question James.
Wiring a Switch for a Bath Exhaust Fan
Application: Wiring a Switch for an Exhaust Fan.
Skill Level: Intermediate to Advanced, best installed by a licensed electrical contractor.
Tools Required: Basic Electricians Pouch Hand Tools and a Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and the switch wiring.
Precaution: The exhaust fan circuit should be identified, turned OFF and Tagged with a Note before working with the wiring and installing the switch.
Understanding Switch Wiring for a Bathroom Exhaust Fan
James, if you have connected all of the three cable wires color to color, then you have created a dead short at the wall switch for the exhaust fan.
- From what you have described, this may be the wiring designations for the cables:
- Cable for Power In – from the circuit breaker.
- Cable for Power Out – to provide power to other devices on the circuit.
- Cable for Switch Control – to the wall switch.
How to Wire a Single Switch for a Bathroom Exhaust Fan
- The key here is to identify the cable that is used for the wall switch, which will basically be a loop from the source power to the switch and then back up to the bath exhaust fan.
- When a 2-wire cable is used for a switch, the white wire is marked with black electrical tape to indicate that it is not being used as a neutral wire. So this cable is the loop from the source of power, to the switch, then through the switch, then back up where it will be connected to the black wire of the exhaust fan.
- The white neutral wires of the bath exhaust fan are connected to the white neutral wires of the power source cables.
More about Wiring a Switch for an Exhaust Fan
- How to Install Bathroom Electrical Wiring
How to Install and Wire a Bathroom Exhaust Fan with Pictures and Step-By-Step Instructions to Guide You.
How to Install a Bathroom Exhaust Fan
- How to Wire a Switch
Wiring a Light Switch – Diagram 1
- Wiring Diagrams
- Fully Explained Light Switch Wiring Diagrams. Detailed Electrical Wiring Diagrams and Pictures assist your Home Electrical Projects.
- Electrical Circuit Breakers
Home Electrical Circuit Breakers
- A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
- Guide to Home Electrical Wire
Electrical Wire for the Home
- Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.
MORE ABOUT THIS TOPIC: