# Split-Buss Electrical Panels

 Understanding Split-Buss Electrical Panels: Dave explains that a split buss circuit breaker panel allows the upper circuits to remain energized while the bottom section is controlled by a separate circuit breaker. .ew_horz_1 { width: 468px; height: 60px; } @media(min-width: 320px) { .ew_horz_1 { width: 200px; height: 40px; } } @media(min-width: 480px) { .ew_horz_1 { width: 300px; height: 60px; } } @media(min-width: 640px) { .ew_horz_1 { width: 468px; height: 60px; } }

## Understanding Split-Buss Electrical Panels

Electrical Question: Dave, the attached picture is a my breaker box in my home. The top two breakers are 50 amp and are 240 Volt.

• The next one is a 30 amp 110. The other six breakers are 20 amps and they are for lights, outlets, etc.
• When I throw the 30 amp, the whole house is dead except the two 50 amp lines, as the 30 amp is my main breaker (the 50 amp lines have nothing plugged into them). Why is this?
• When you throw the main should it shut off power to everything?
• Also is the 30 amp main big enough for those 6 20 amp breakers?
• I seem to blow the 30 a lot during the summer running two room-air conditioners

This electrical troubleshooting question came from: Larry, a Homeowner from Linwood, MI
See more about Home Wiring for Michigan

PLEASE NOTE: The following information applies to this question only. In normal situations circuit breakers should never be exchanged for a larger size.

Thanks for your electrical troubleshooting question Larry.

Understanding Split-Buss Electrical Panels

• Larry, you have a split buss circuit breaker panel which allows the upper circuits to remain energized while the bottom section is controlled by the 2-pole 30 amp breaker. The wires size linking the 2-pole circuit breaker to the bottom section of the panel will support a larger size circuit breaker, in fact one of the 2-pole 50 circuit breakers could be swapped with the 2-pole 30 amp circuit breaker allowing more amperage to the bottom section of this panel.
• A split buss panel such as this is not common for most homes these days, but for this application at one time it allowed the upper 2-pole circuits to remain on where they may have fed large equipment that was required to remain on while the lower circuit were turned off.
• One common application for a similar set up would be for a 2-pole circuit to remain on for a well pump where in the case of a fire all the electrical circuits can be De-energized but the water supply or pump remains energized.

The Following will assist you with Home Electrical Systems

220 Volt Wiring Diagram

Electrical Junction Boxes

Circuit Breakers

House Wiring Circuits and Circuit Breakers

### House Wiring Circuits and Circuit Breakers

This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electrical Panel Circuit Listing

circuit breaker

Electrical Wiring Protection using Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.

 Learn How to Wire it Right with my Complete Guide to Home Electrical Wiring Perfect for Homeowners, Students, Handyman, Handywomen, and Electricians Includes: Wiring GFCI Outlets Wiring Home Electrical Circuits 120 Volt and 240 Volt Outlet Circuits Wiring 3-Wire and 4-Wire Electric Range Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet How to Troubleshoot and Repair Electrical Wiring Wiring Methods for Upgrading Electrical Wiring Electrical Codes for Home Electrical Wiring ....and much more. » Click here to learn more about Home Electrical Wiring «