Replacing an Outlet with a GFI Receptacle
By Dave Rongey - Summary:|
How to Replace an Outlet with a GFI Outlet or GFCI Receptacle: Identifying Wires for GFI Connections.
If this is your first visit, be sure to sign up for your Free Electrical Tips and eBook.
Your Comments and Electrical Questions are always welcome.
Wiring Outlets and GFI Receptacles
- I understand the Line and Load principle and the black wire to brass screw and white wire to silver screw.
- I’m confused by the fact that of the four wires coming from the box, THREE are white and only ONE is black?
Any assistance is appreciated. Regards,
This electrical question came from: John, from Everett, Massachusetts.
Thanks for your electrical wiring question John.
How to Replace an Outlet with a GFCI Receptacle
Application: Replacing Outlets with GFCI Outlets.
Skill Level: Beginner to Intermediate – Best if wired by a Licensed Electrical Contractor.
Tools Required: Basic Electricians Pouch Hand Tools and a Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and the number of GFI outlets that will be installed.
Precaution: Identify the affected outlet circuits at the electric panel, turn them OFF and Tag it with a Note before working with the outlet wiring.
Materials: Make sure to use materials of the same amperage and voltage rating as the electrical circuit.
Notice: Installing additional GFCI Outlet Wiring should be done according to local and national electrical GFCI Codes with a permit and be inspected.
Identifying Wires for GFI Connections
- Typical Outlet Wiring Example
- John, it would be good to know what the orientation or wiring connections are for the original outlet, however in most cases there are a set of wires from each cable such as Black, White and Bare or Green, Power, Neutral and Ground respectively.
- Identify Odd Wires
- The odd white wire which you have described requires identifying exactly what it’s purpose is in order to make the proper connection.
- GFCI Line and Load Connections
- When the GFCI receptacle supplies power to other outlets then they will be wired to the LOAD terminal connections of the GFCI receptacle. The LINE area is designated for the incoming power of the circuit.
More about Wiring GFI Outlets
GFI Outlets and Receptacles
Step by Step Pictures with Easy Wiring Diagrams and Installation Guide for wiring GFI Outlets.
GFCI and GFI Wiring Diagrams
The features and benefits of GFCI outlets and receptacles will give you a clear understanding of the importance why these safety devices are required by code to help protect you and your family against accidental electrical shock hazards.
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.