Question – Range Circuit Limitations
Electric range circuits have limitations for what they can be used for.
Kitchen Receptacle Outlet Circuits
Can I use an existing 10-3 wire from the range to wire a combination switch and receptacle?
If the range is still in use then No you cannot use this circuit.
Typically a lighting or receptacle circuit would be 15 or 20 amps 120 volt. Your range, being on the 10-3 is rated at 30 amps 220 volts.
Sounds like you may need to either find another circuit that can be used or have another circuit installed and sized depending on the load which you have in mind.
Wiring a Light Switch – Diagram 1
Fully Explained Light Switch Wiring Diagrams. Detailed Electrical Wiring Diagrams and Pictures assist your Home Electrical Projects.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Wiring a Kitchen Range Power Cord
Fully Described Electric Range Installation with a typical 220 Volt electric power cord wiring system. You may find yourself with either a 3-wire or 4-wire electric range. Lets look at how the electric range is wired and what to do if your cord does not match the plug.
You identified your project to be about Outlet Wiring, so you might find this information useful:
Wiring Electrical Outlets
Fully Explained Photos and Wiring Diagrams for Wiring Electrical Outlets with Code Requirements for most new or remodel projects.
|«||Question – Attic Insulation and Wiring »|
Browse other questions in the following categories:
Voltage and Amperage Limitation Questions
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
See more about Electrical Wiring in Your Local Area