Filed under: Outdoor Lighting »4 Comments «
|« The Difference Between a Wall Outlet and a Floor Outlet||Why Older Homes Have Diming Lights »|
PVC Conduit and Electrical Wiring For Outdoor Lighting
©Copyright Dave Rongey - Summary:
Planning Circuits and Switching for Outdoor Lighting: The key is to plan your circuits and switching ahead so you can size your conduits and junction boxes accordingly. Understand that junction boxes may be used for outlets or switches too.
Outdoor Lighting Circuit Wiring
Electrical Question: Am installing a very large patio floor but want to install underground wiring that would allow for future outdoor lights and one box.
- Am using 3 strands of individual 12 AWG electrical wire and housed in Sch 40 grey PVC conduit.
- I’m unsure of how to run the electrical wiring from one light (or box) to the next.
- Appears as if I’d need a 3-way tee and junction box to continue the wiring run – but suspect that’s not appropriate.
Background: Ross, a Homeowner from Collegeville, Pa.
Thanks for your electrical wiring question Ross.
Planning Circuits and Switching for Outdoor Lighting
Application: Outdoor Lighting.
Skill Level: Intermediate to Advanced – Depends on the number of lights that will be required within the circuit wiring.
Tools Required: Basic Electricians Pouch Hand Tool, Voltage Tester, trenching equipment or shovels .
Estimated Time: Depends on personal level experience and ability to work with tools and the condition of the soil where PVC conduit will be installed.
Precaution: Identify the lighting circuit or power source, turn it OFF and Tag it with a Note before working with the wiring and connections.
Notice: Installing additional electrical wiring for outdoor lighting should be done according to local and national electrical codes with a permit and be inspected.
Installing Wiring for Outdoor Lighting
- Connecting PVC conduit electrical wiring is much the same as Romex wiring.
- You will need to bring up the PVC conduit to a desired location and extend it up to a junction box location and make your loops from that point on.
- Additional under floor loops can be installed as necessary.
- The key is to plan your circuits and switching ahead so you can size your conduits and junction boxes accordingly. Understand that junction boxes may be used for outlets or switches too.
More about Electrical Circuit Wiring
I have provided the following resources that lead to fully detailed information on this website that will assist you with your electrical wiring question:
For more information about Electrical Wiring
Home electrical wiring projects with pictures and wiring diagrams.
This link is helpful as a Homeowner
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.