Kitchen Countertop Receptacles NEC 210-52
What is the NEC Code for Kitchen Counter Top Outlets? The Electrical Code Requirements for Kitchen Counter top Receptacle Circuits.
NEC Code for Kitchen Counter top Receptacles
Electrical Question: What is the NEC Code for Kitchen Counter Top Outlets?
Can you please clarify the NEC 210-52 Electrical code for kitchen outlets.
- The NEC 210-52 Code states that receptacles installed in the kitchen to serve counter top surfaces shall be supplied by not less than two separate small appliance branch circuits.
- Does this mean that a circuit needs to have 2 supplies or 2 or more Receptacles per circuit?
This electrical wiring question came from: Jim, a Student from Rapid City, South Dakota.
See more about Home Wiring for South Dakota
Additional Comments: Great site, helped me a lot with data com.
Thanks for your electrical wiring question Jim.
Kitchen Counter Top Receptacle Circuits
The following is an explanation of the Electrical Code Requirements for Kitchen Counter top Receptacle Circuits:
- Electrical Code Requirements for Kitchen Counter top Receptacle Circuits
- The NEC code requires at least two separate circuits to the kitchen counter top receptacles.
- These receptacle outlets must must have GFCI protection for each circuit.
- The number of receptacle outlets on each circuit is typically determined by the length of the counter top area.
- If the counter top is found on the left and right side of the sink, then one circuit can feed the left side, and the other circuit can feed the right side.
- The layout of the circuits and receptacles will be determined by the exact layout and design of the kitchen.
- The kitchen counter top circuits are separate from additional circuit requirements for items such as the refrigerator, dishwasher and the disposal, etc. , as these items all have their own circuit requirements.
More about Kitchen Counter Top Outlet Circuits
- Electric Circuit Listing
- The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
- How to Install Kitchen Electrical Wiring
- Kitchen Electrical Wiring
- Fully Explained Photos and Wiring Diagrams for Kitchen Electrical Wiring with Code Requirements for most new or remodel projects.For more information about Outlet Wiring
- How to Install Electrical Outlets
- Wiring Electrical Outlets
- Fully Explained Photos and Wiring Diagrams for Wiring Electrical Outlets with Code Requirements for most new or remodel projects.
Electrical Code Articles for Home Wiring
Electrical Code Directory covering requirements for kitchen outlet circuits.
|« NEC Electrical Code for Re-Identifying Ungrounded Conductor||Electrical Code and Buried UF Cable »|
Browse other questions in the following categories:
NEC 210.52 Countertop Circuits
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
See more about Electrical Wiring in Your Local Area