Is There an Electrical Problem When Lights and Appliances Go Off And On?
By Dave Rongey - Summary:|
Most often this is the symptom of a deteriorating connection that is occurring most likely at the electrical…
Electrical Question from John about Repairing Electrical Wiring
Background: John, a Handyman from Flint, MI
Additional Comments: Great site!
Thanks for your electrical question John. Most often this is the symptom of a deteriorating connection that is occurring most likely at the electrical panel. The suspect areas are the neutral wire terminations, a main breaker that is starting to go bad, a main circuit breaker connection to the buss, a main service termination in a lug, or a splice that is going bad at the main overhead electrical service connection from the electrical utility company. A condition such as this will deteriorate over time and has the potential of requiring a major electrical repair job. The first thing I recommend is to call your electrical utility company and explain the occurrences. Most utility companies will dispatch a service technician who will inspect their side of the service wiring. If they do not find any problems then I would call a licensed electrical contractor who can perform a series of inspections and tests which will identify the problem. This could be a serious condition which requires professional attention.
The Following links will assist you with your electrical question:
For more information about Repairing Electrical Wiring
This link is helpful as a Handyman
Make sure not to miss these Resources for: Electrical Safety
Home Electrical Safety
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area