Filed under Dryer, Dryer Circuit, Electric Wiring, Electrical Safety
How to Wire a Dryer Outlet
By Dave Rongey - Summary:|
Electric Dryer Outlet Problems and How to Fix Them: Problems with Dryer Outlet Wiring, Dryer Circuit Wiring.
Electric Dryer Outlet
- 220 Volt Dryer Outlet
The wire on my dryer started burning next to the box on the electrical outlet. I changed the wire on the dryer and the 220volt outlet on the wall.
- Dryer Did Not Work
I plugged it in and the dryer didn’t work. I bought a circuit tester and the tester proved that there was electricity coming from the 220 volt outlet. So I bought a new dryer and when I plugged it in, the new dryer did not work.
- New Replacement Dryer Did Not Work
The company send me out a new dryer, when it arrived, I plugged it in and that didn’t work either.
- Replaced the Dryer Circuit Breaker
I bought a new circuit breaker, and that didn’t work either.
- Dryer Outlet Wiring
Should I cross the wires up on the 220 volt outlet? I’m afraid that if I do so that I could start a fire or I could burn or damage the dryer. What could be possibly wrong.
Please guide me or help me with this matter.
Thanks in advance.
This home electrical wiring question came from Tyrone.
Thanks for your electrical troubleshooting question Tyrone and Wayne.
Wiring an Electric Dryer Outlet
Application: 220Volt Dryer Cord and Dryer Outlet Wiring.
Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrician.
Tools Required: Basic Electricians Pouch Hand Tools and a Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and the available access to the dryer cord electrical connection box.
Important: Identify the dryer circuit, turn it OFF and Tag it with a Note before working with the dryer receptacle outlet or cord wiring.
Problems with 220 Volt Electric Dryer Outlets and How to Fix Them
With a problem such as this the dryer circuit should be turned OFF and the dryer should NOT be plugged in until the wiring has been corrected because incorrect wiring of a 220 volt dryer outlet may result in a Electrical Shock Hazard.
Evaluate and Correct the Problem with the Dryer Circuit
- Inspect and Repair the Circuit Wiring of the Dryer Outlet
It is stated in this question that the wire on the dryer started burning next to the box on the electrical outlet, therefore it is essential to determine the cause which resulted in the burnt wire at the outlet. The dryer circuit and wiring components should all be carefully examined to discover the fault, and then repairs should be performed as need. The following information will describe the typical wiring of a dryer circuit and receptacle outlet.
Wiring Connections for a 220 Volt Dryer Outlet
- Verify the Wiring Connections to the Dryer Outlet
It is very possible that when the dryer receptacle was rewired that the wiring assignments are not correct. The wiring should be corrected using a voltage tester to positively identify each wire of the dryer circuit if the wires are not already clearly marked or indicated. Once the circuit wires have been identified then the connections to the dryer receptacle must be checked to make sure the receptacle is wired correctly.
- 220 Volt Dryer Circuit
Electric dryers that are 220 volts typically require a dedicated 30 amp circuit containing a 4-wire circuit for new installations, and older homes may have a 3-wire circuit.
- The 3-wire 240 volt circuit has one ground wire and two power wires, Line 1 and Line 2, of 120 volts each when testing the Line to ground, and 240 volts when tested Line 1 to Line 2.
- The 4-wire 240 volt circuit is the same as the 3-wire circuit except that it has a separate Neutral wire, which makes this a 4-wire circuit. 4-Wire circuits are required for most new electric dryers, however they may be adapted for use with some older 3-wire dryers.
- Wiring a 240 Volt Dryer Receptacle
On each of these 30 amp 240 volt dryer receptacle outlets there will be indications for the terminals where the circuit wires are to be located:
- The Line 1 wire is attached to the terminal with the X designation.
- The Line 2 wire is attached to the terminal with the Y designation.
- NOTE: Some brands of 240 volt outlets may specify Line 1 and Line 2.
- The ground wire is attached to the terminal with the GREEN, Vert or the Ground Symbol
- The Neutral wire is attached to the terminal designated as White or Blanc.
More about Wiring an Electric Dryer
3-Wire and 4-Wire Configurations for Clothes Dryers
See an electric dryer installation with a typical 220 Volt electric power cord wiring system. You may find yourself with either a 3-wire or 4-wire electric dryer, or a 3-wire or 4-wire outlet. Lets look a how the electric dryer is wired and what to do if your cord does not match the plug.
Electrical Circuit Wiring
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Home Electrical Panel Circuit Listing
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Wiring 220 Volt Electrical Outlet
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how electrical outlets for the home are wired.
Understanding Electrical Testers
When working on home electrical wiring using voltage testers can play an important part in electrical safety. Electrical testers enable you to identify electrical circuits and help prevent the possibility of accidental electrical shock.
Home Electrical Safety
Electrical Safety Articles covering several topics of home electrical safety and Do-It-Yourself Electrical Safety.
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.
|« Adding an Electric Panel and Circuits||Why a Ceiling Fan Trips the Circuit Breaker »|