Filed under Electrical Wiring
How to Wire a 3 Phase Air Compressor
By Dave Rongey - Summary:|
Wiring a 3 Phase Motor for an Air Compressor: The Basic Requirements for Wiring Electric Motors, 3 Phase Motor Circuits
Air Compressor Electric Motor
This electrical wiring question came from Cody, in Enid, Oklahoma.
Thanks for your electrical wiring question Cody.
Wiring a 3 Phase Motor for an Air Compressor
The Basic Requirements for Wiring Electric Motors
- Every motor should have a name plate which is typically attached on the side or end of the motor. The information found on the label tells all about the motor size and electrical requirements. To stay on track with this question, the shop where the motor is to be installed must have an electrical service which supplies either 3 phase 230 volts, or 3 phase 460 volts.
Electrical Service Panels
- Just like electric motors, an electrical service panel should be equipped with a label which is attached either on the cover or inside the door. The information on this label will be specific to the make and model of the electrical panel along with the voltage and amperage rating. Here in the USA, a typical home electrical panel may be 120/240 volts 125 amps. The actual amperage capacity of the panel is best known by examining the Main Disconnect or Main Circuit Breaker, which will have the amperage rating identified, such as on the breaker handle.
Electrical Power for 3 Phase Motors
- Without getting too technical, a 3 phase electrical service panel will produce 3 separate lines of electrical power. A 120/240 volt single phase panel found at a home or shop can only provide up to two separate lines of power, therefore this type of electrical service could not provide the necessary power for a 3 phase motor.
3 Phase Motor Circuits
- As described above, a typical 3 phase motor circuit will have 3 separate insulated wire conductors for the power and the ground wire. A neutral wire is not required for a 3 phase motor.
A Summary of Wiring 3 Phase Motors
- Identify the required voltage and amperage.
- Determine if the electrical service panel has the same voltage and available amperage capacity.
- Electric motors are typically wired to a motor controller or motor starter which is sized appropriately to the horsepower of the motor and has thermal overload protection.
More about Electrical Circuit Wiring
House Wiring Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electrical Panel Circuit Listing
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.
|« How to Replace a Thermostat||Kitchen Range Circuit »|