How to Repair a GFI Outlet Circuit
By Dave Rongey - Summary:|
Troubleshoot and Repair GFI Outlet Circuit Wiring: I have a problem with the GFCI circuits in my home, Example of How to Test a GFI Circuit.
Steps for Testing a GFCI Outlet Circuit
- The end of the GFCI line is in the garage and before that the bathroom which joins the garage. I cannot get power to either.
- The line coming out of my panel leads to a GFCI outlet, about one foot away.
- There’s power coming out of the “load” line.
- Here’s the problem, sometimes I do get power to both outlets in the bath and garage, then, when I plug in a device (lead light) in the garage the light goes on initially then dims and goes out. Then I got no power to the bath or the garage.
- Power is still on coming out of the GFCI outlet next to the panel box.
- Fearing there might be a wiring problem, maybe to a switch, I’ve turned all switches in the house on and that doesn’t connect.
Thank you for your advice.
This electrical wiring question came from: Jerry, in NY, New York.
Thanks for your electrical wiring question Jerry.
Troubleshoot and Repair GFCI Outlet Circuit Wiring
- Skill Level: Intermediate to Advanced.
- Tools Required: Basic Electricians Pouch Hand Tools a Voltage Tester or Plug-In Circuit Analyzer.
- Estimated Time: Depends on personal level experience, ability to work with tools, the extent of the electrical repairs, the number of outlets that are affected and access to each location.
- Precaution: Identify the GFCI outlet circuit, turn it OFF and Tag it with a Note before working with the wiring.
How to Test a GFI Circuit
When the GFI circuit seems to be partially working or not working at all here are some things to double check to get the GFCI working again.
- Check for Loose Wires
Make sure there are no loose wires within the circuit, especially the white neutral wire.
- Incoming Power Source: The LINE
Make sure the incoming power source to the GFCI outlet are attached to the LINE side as indicated on the back of the receptacle.
- Outgoing Power Source: The Load
Make sure the outgoing circuit wiring is connected to the LOAD side of the GFCI Outlet.
- LINE and LOAD Wiring
Both the black and white wires must be connected separately into the appropriate terminals of the LINE and the LOAD side of the GFCI Outlet or GFI Receptacle.
- A Bad GFI
If the wiring connections are correct and the circuit voltage is normal then the GFCI outlet may be faulty and should be replaced.
- Checking the Circuit Polarity
The integrity of the GFI circuit wiring may be tested for voltage by temporarily removing the GFCI outlet and splicing the wires through and then testing the voltage and polarity at each receptacle outlet of the same circuit. If the voltage readings and polarity test is normal then the GFCI is faulty or the connections to the GFCI were incorrect.
- Plug-In Circuit Analyzer
A plug in circuit analyzer will be helpful to determine the correct wiring of the circuit and help detect circuit faults.
Important Note about Ground Fault Circuit Interruption:
Both GFI and GFCI are basically the same and both provide protection against ground faults by interrupting the electrical circuit by sensing voltage that passes to a ground source.
More about Wiring a GFCI
- How to Wire GFCI Outlets
GFCI and GFI Wiring Diagrams
- The features and benefits of GFCI outlets and receptacles will give you a clear understanding of the importance why these safety devices are required by code to help protect you and your family against accidental electrical shock hazards.
This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.
- Electrical Outlet Wiring
Wiring Electrical Outlets for the Home
- Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
- Basic House Wiring Circuits
House Wiring Circuits and Circuit Breakers
- This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
- Using Testers to Identify the Cause of why Electrical Power has been Lost
Testers Help Determine Conditions that Lead to Electrical Power Loss
- Troubleshooting to Find Out Why Your Home Lost Power
How to Identify Lost Power
- Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
Types of Electrical Testers
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.