How To Make an Underground Cable Splice
I hit an un-located 2″ conduit with a trencher, breaking the conduit and pulled about 40′ of 3/0 THHW coated neutral wire out of the conduit…
Making Underground Cable Splices Accessible
Question: I hit an 2″ conduit that we could not locate with a trencher, breaking the conduit and pulled about 40′ of 3/0 THHW coated neutral wire out of the conduit. Can I pull a new length of 3/0 into the conduit and splice it to the undamaged portion of cable. Can I then install an expansion sleeve over the splice point to provide conduit continuity.
This electrical question came from: David, a Contractor from Memphis, Tennessee.
Additional Comments: Very effective and easy to use.
Thanks for your electrical question David.
David, if you make a splice with the cable it should be made accessible. It would be best to pull in the new cable and install a christy box in the location of the splice.
The Following links will assist you with your electrical question:
Electrical Junction Box Splice
Electrical junction box splices can be made safely when you understand the method. This example will show you how its done step by step and shows how to make a junction box splice and the related electrical codes.
For more information about Electrical Code
Home Electrical Code
Electrical Code Directory covering afci-circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, electrical-gfci, electrical-grounding, electrical-project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-codes and smoke-detectors.
|« Low Volt Relay Control Wiring Diagram||Splicing A Short Cable In A Panel »|
Browse other questions in the following categories:
Electrical Wire Splice
Or Ask Dave a Question
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.