Filed under Electrical Wiring, Generator Installation, Home Generator
How to Ground a Home Generator
By Dave Rongey - Summary:|
How to Ground a Generator and the Home Electrical System: Bonding the Generator to the Grounded Electrical System of the Home.
Grounding a Home Generator
Existing Generator Installation:
The Outside Wall Has a Male Connection Receptacle L14-30p
- I run thru a pass thru in the kitchen wall. On the inside wall is a 30Amp fused disconnect which then goes to an outlet box containing my L14-30r. Then from L1430 the power goes to my two GFCIs, then 120 volt extension cords. I have no desire to ever use a transfer switch and yes am fully aware never to BACK FEED branch circuits. In emergency I only want power for refrigeration, a small appliance and use the internet and two lights.
- My question is about grounding. I run a #6 ground from the generator’s ground lug THRU AN OUTLET BOX on the outside into my basement and tied it with a Burndy into my Grounding electrode system #6 to a water pipe and 2 ground rods. Is this best? Would it be better to drive A SEPARATE Ground Rod at the generator?
- My current reservation is that in the event of a lightning strike to the generator am I “inviting” the strike into my home’s GES, Grounding Electrode System? Thus a separate rod might help somewhat? Might avoid a hit to my GES with a separate ROD?
- Also in the event of a fault inside the generator how does the fault clear…If a fault doesn’t trip the breaker could the ground (GES) become energized & back to the utility neutral/transformer. Thus would it be better to either use a separate ground rod or my GES? I am aware that the generator’s frame is a ground. Am I over doing this by grounding to GES or separate rod?
- Lastly,another concern on my set up: Would any current in the event of a fault or lightning strike possibly get back to the electric utility pole transformer in addition to passing to ground thru my home GES. Thus making a separate rod a better choice?
Thanks for your availability & patience in helping. I have yet to find an example of anyone using my exact set up on-line and really would like to know if I should change anything.
This home electrical repairs question came from: Charlie, from Boston, Massachusetts.
Thanks for your electrical troubleshooting question Charlie.
How to Ground a Generator and the Home Electrical System
Skill Level: Advanced – Licensed Electrical Contractor, Not Recommended for Homeowners.
Tools Required: Electricians pouch of hand tools and the various power tools necessary for installing the generator and transfer switch.
Estimated Time: Depends on the type and size of the generator and transfer switch and the available access to the project area.
Important: Installing a generator and transfer switch or altering the home electrical system must be well thought out and performed with a permit with all work being inspected.
Bonding the Generator to the Grounded Electrical System of the Home
- Installing an additional ground rod for a home generator would not be necessary when there will be an electrical connection to the home panel.
- Installing a ground wire that is attached to the ground terminal of the generator or an internal bond, which is then attached to the bonded ground system of the home electrical panel is required.
- In the event of a lighting strike, the strike will take the path of least resistance to the earth ground which should always be the home electrical ground system which has been installed according to applicable local and national electrical codes.
- The path and power of a lightning strike is unpredictable due to many environmental factors, however the required home Ground Electrode System GES is the best way to direct the lighting strike to the earth ground. This will also help prevent the lightning strike from traveling back to the utility transformer power pole.
More about Home Generators
Home Electric Generators
- This series covers a wide variety of topics all about home generators including sizing, selecting, connecting and safely operating this all important addition to your home.
The Importance of a Generator Transfer Switch
Electric Circuit Listing
- The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
- Electric Circuit Breakers
- A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Electrical Grounding Methods and Requirements
- Listing of electrical codes for grounding with examples of electrical grounding codes for home electrical wiring.
- Electrical Calculations and Formulas
Home Electrical Codes
Electrical Code Directory covering Electrical Grounding, Electrical Services, Electrical Wiring and more.
Learn How to Wire it Right!
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.
|« Causes of Lost Power to GFCI Outlets||Replacing Old Smoke Detectors »|