How Do I Install Electrical Wiring For A Pond Pump?
By Dave Rongey - Summary:
Wiring a pond pump back to house to junction box on outside foundation through wall and…
Electrical Question from Larry about Wiring A Pond Pump
Background: Larry, a Homeowner from Milford, OH USA
Thanks for your electrical question Larry. From the house junction box I would recommend installing aÂ half or three quarter inch PVC conduit in a trench to the required depth of 18 inches which would end at the desired location at the pond. The larger three quarter inch size is not that much more expensive and will allow you to pull the wire through much more easily.Â An alternative is to install a Direct Burial Type UF Cable at a depth of 24 inches which would be protected with PVC at each end of the bottom of the trench, up to the junction box locations where the cable emerges. The junction boxes and associatedÂ materials must be rated NEMA 3-R for outdoor use. The circuit must be GFCI protected and weather proof coversÂ which can accommodate the pump cord being plugged in and covered as well. The wire gauge must be sized the same as the wire at the house. This project should be installed with a permit and inspection. Please see the Electrical Codes link below for more information.
The Following links will assist you with your electrical question:
For more information about Electrical Wiring
This link is helpful as a Homeowner
Make sure not to miss these Resources for: Wiring Diagrams
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.
MORE ABOUT THIS TOPIC: