Filed under Electrical Wiring
How to Convert a Circuit to be Used for a Sub-Panel
By Dave Rongey - Summary:|
Converting a 220 Volt Circuit Cable for a Sub-Panel: How to Install a Sub Panel Using an Existing Circuit, Sub Panels Require a 4-Wire Feeder Cable with a Separate Dedicated Neutral.
Converting a 220 Volt Circuit Cable for a Sub-Panel
- We have since switched to N.G.
- My question is can I reroute the 220 volt cable to the basement and use it for the power to a sub-panel?
- I only have one receptacle in the basement.
Thanks for the info.
This electrical wiring question came from: Buck, from Emmett, Idaho.
See more about Home Wiring for Idaho
Thanks for your electrical wiring question Buck.
How to Install a Sub Panel Using an Existing Circuit
Application: Electrical Wiring for a Panel.
Skill Level: Intermediate to Advanced – Best performed by a licensed electrician.
Tools Required: Electricians pouch of hand tools and the various power tools necessary for installing the sub-panel.
Estimated Time: Depends on the type and size of the panel and available access to the project area.
Precaution: Any existing electrical wiring within the immediate area that may interfere with the installation of the sub panel should be identified and turned OFF and Tagged if necessary.
Notice: Installing additional electrical wiring and a sub-panel should be done according to local and national electrical codes with a permit and be inspected.
Sub Panels Require a 4-Wire Feeder Cable with a Separate Dedicated Neutral
- 120/240 Volt Circuits
- A typical sub panel that will be used to supply power for 120 volt circuits.
- Typical 120 volt circuits may be receptacle outlets, lighting, smoke detectors, or any other 3-wire 120 volt device.
Circuit Disconnect for 240 Volt Equipment
- 240 Volt Circuits
- A Dedicated Neutral wire conductor is not required for 240 volt circuits for equipment that does not require a neutral.
- Typical 240 volt equipment may be a hot water heater, air compressor, welder, or any 3-wire 240 volt equipment.
- The circuit amperage requirements must be within the range of the amperage rating of the cable to be used for the circuit.
The total connected load of the circuits that would be added to a sub-panel must be 80% of the amperage rating of the cable supplying power to the sub-panel.
More about Electrical Wiring for Panels and Circuits
House Wiring Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Home Electrical Circuits
Electric Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Home Electrical Codes
Electrical Code Directory covering methods of electrical circuit wiring and electric panels.
Learn How to Wire it Right with my
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.
|« Control Two Outdoor Light Fixtures with a Motion Detector||How To Add an Electrical Outlet »|