GFCI Receptacle, GFCI Breaker or Both
By Dave Rongey - Summary:|
Is a GFCI breaker required if GFCI receptacles are present in the bathrooms and kitchen? Does having both receptacle and breaker GFCI rated provide greater protection…
Will a GFCI Breaker and GFCI Receptacle Be Safer?
This electrical question came from: Mike, a Property Manager from Phoenix, AZ
Thanks for your electrical question Mike.
Mike, either the GFCI Receptacle or a GFCI Breaker is fine. Having both will not provide any more protection due to the threshold level that is designed into the basic GFCI devices. There are more sensitive GFCI Circuit Breakers that are required in areas such as where electric heating cables are used to melt snow and ice.
The Following links will assist you with your electrical question:
See more about Electrical Wiring for Arizona
Kitchen Electrical Wiring Requirements
This wiring diagram and pictures explain the basic kitchen electrical code wiring requirements required for most new or remodel projects.
Bathroom Electrical Wiring Requirements
This wiring diagram and pictures explain the basic bathroom electrical code wiring requirements required for most new or remodel projects. Give your bathroom a face lift when you enhance the electrical devices that will bring out the best in you. Make your eyes sparkle with get a breath of fresh air when you install one of these smart upgrades.
For more information about GFCI Wiring
This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.