Generator ATS Provides Power During Partial Power Loss
By Dave Rongey - Summary:|
How a Generator Automatic Transfer Switch Works and is a Very Important Part of the Home Generator System
A Generator HTS/ATS Can Provide Power When One Leg Of Power Is Lost
I am assuming just one phase went out, and so the generator kicked on and has been supplying power ever since. Now the reason I am thinking just one phase went out is because we have two HTS transfer switches. One has standby operation lit with utility power not lit, and the other has utility power lit and the switch position is utility. Is it possible that there is a problem with the power company that just one of the phases are down? And if so, should I report this as a power outrage?
Background: Eric, a Other from Stow Ohio
Thanks for your electrical question Eric.
How a Automatic Generator Transfer Switch Works
- Eric, I don’t believe this is a problem with the utility company because the power failure has affected only one third of the building.
- I would check the main circuits upstream from the functioning HTS/ATS where you may find that you have a tripped breaker or lost one leg of the three phase power, therefore the ATS is doing it’s job by automatically providing generator power due to a electrical circuit failure.
This series covers a wide variety of topics all about home generators including sizing, selecting, connecting and safely operating this all important addition to your home.