Electrical Wiring for a Garage Workshop
Installing an Electric Panel for a Detached Garage: Electric Codes for a Detached Garage Panel, Can I use a Main Lug Only Electric Panel Load Center for a detached garage?
Garage and Workshop Electrical Wiring
Electrical Question: Can I use a Main Lug Only Electric Panel Load Center for a detached garage?
- I intend to electrify a detached garage, which is about 60 ft. from the house panel.
- The Power needs will be convenience outlets and lights for a workshop.
- The project and circuits to be installed are the following:
- I will use two 30Amp circuits, 3 wire + equipment ground, #10 wire, in 3/4″ underground PVC conduit to provide the power to the garage.
- I plan to install a 30Amp load center in the garage with two 20Amp circuit breakers.
- Can I use an MLO or Main Lug Only Load Center or do I need a Main Disconnect as well?
This electrical question came from: Jim, a Property Manager from Urbana, Illinois.
Thanks for your electrical question Jim.
Installing an Electric Panel for a Detached Garage
Application: Installing an Electric Panel for a Garage or Workshop.
Skill Level: Advanced – Best installed by a Licensed Electrical Contractor.
Tools Required: Electricians pouch of hand tools and the various power tools necessary for the specific method of electrical service installation.
Estimated Time: Depends on the type of panel, the location, and available access to the project area.
Precaution: This is an extensive project. Working in an electric panel has shock and arc flash hazards and should be performed by a Certified Electrician or Licensed Electrical Contractor.
Notice: Installing an Electrical Panel should be done according to local and national electrical codes with a permit and be inspected.
Electric Codes for a Detached Garage Panel
Jim, because the garage is detached it would be best to have a main disconnect, however please see the following electrical codes that will apply to your question.
- The panel may not have more than 6 circuit breakers.
- If the number of circuit breakers are more than 6 then a main disconnect is required.
- NEC Electrical Code Reference articles 225.31, 225.32, 225.33, 225.36.
More about Wiring a Garage or Workshop
Home Electrical Codes
- Electrical Code Directory covering electrical boxes, electrical circuit, electrical code outlets, electrical grounding, electrical services, electrical underground, and electrical wiring methods.
- Garage Electrical Wiring
- Garage electrical wiring diagram and considerations for wiring garage circuits, complete with pictures.
- Careful planning for your garage with immediate and future equipment considerations will help you understand how to size your electrical circuit requirements.
- This information will help as an garage electrical wiring guide.
- House Wiring Circuits and Circuit Breakers
- This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
- Electric Circuit Listing
- The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
- Electrical Wiring Protection using Circuit Breakers
- A guide to home electrical circuit breakers and how they work to protect your electrical wiring.
- When properly installed, your home electrical wiring is protected by a circuit protection device.
- Electrical Wire for the Home
- Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
|« Wiring a Photocell for an Outdoor Light Fixture||How to Install Wiring for a Ceiling Light Fixture »|
Browse other questions in the following categories:
Garage Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
See more about Electrical Wiring in Your Local Area