Electrical Code for Bonding Ground Wires
How to Splice Electrical Wires and the Ground: For projects where you are extending the wiring of an existing circuit then the additional wire size must match that of the circuit you are branching from or splicing. Electrical junction box splices can be made safely when you understand the method.
NEC Code and Bonding Ground Wires
Electrical Question: I believe I read in the NEC that you should never bond different sized wires together (e.g. never bond a 14-gauge wire into a 12-gauge circuit.
- This would imply that I can’t add a simple switched light fixture into an existing 20-amp circuit unless I wire it with 12-gauge wire.
This electrical wiring question came from: Gary, a Handyman from Lake Worth, Florida.
Additional Comments: Very useful resource.
Thanks for your electrical wiring question Gary.
How to Splice Electrical Wires and the Ground
- The NEC Electrical Code that you may be referring to does not apply to your electrical wiring application.
- Yes – you can splice a 14 gauge ground wire from a light fixture to a #12 gauge ground wire in the light fixture junction box.
- For projects where you are extending the wiring of an existing circuit then the additional wire size must match that of the circuit you are branching from or splicing.
- Be sure to use the right size wire connector for the wire gauges and number of wires that will be spliced.
Electrical Junction Box Splice
Electrical junction box splices can be made safely when you understand the method. This example will show you how its done step by step and shows how to make a junction box splice and the related electrical codes.
More about Home Electrical Wiring
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Electric Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
|« How to Prevent Generator Overload and a Tripped Circuit||How to Wire a Generator Transfer Switch »|
Browse other questions in the following categories:
Bonding Ground Wires
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
See more about Electrical Wiring in Your Local Area