# Converting a 120 Volt Motor to 240 Volts

 How to Convert the Electrical Circuit Voltage for a Motor: There are multiple problems here. You and the electrician did not discuss exactly what the 240 volt outlet would be used for. This is a big mistake, and I’m amazed that the electrician did not ask you what the circuit would be used for.

Converting the Electrical Voltage of a Motor
Electrical Question: I have an old Craftsman table saw that can run on either 120v or 240v with a minor change within the motor, which has three input wires – a ground and two lines.  For some years, I’ve operated it at 120v, but it lacks the power to rip certain hardwoods.

• Recently, in conjunction with another project, I asked a licensed electrician to install a 240v outlet in my garage, but wasn’t specific about what I wanted.
• He installed a 4-wire outlet, and provided me with a matching plug, and I thought it would be a piece of cake to connect up the table saw motor.
• I bought a  double-pole, single throw switch, which has two terminals marked Load and two marked Line.
• After checking the switch with my ohm meter, I connected the switch and the motor but found that when I turned the switch on, the circuit breaker blew.
• I ran the black wire from the plug to a Load terminal, then a wire from the corresponding Line to the motor, and similarly for the red wire from the plug.

Clearly, I’m missing something, but what?
Background: Michael, a Handyman from Sherwood, OR

Thanks for your electrical wiring question Michael.

### How to Convert the Electrical Circuit Voltage for a Motor

• There are multiple problems here. You and the electrician did not discuss exactly what the 240 volt outlet would be used for. This is a big mistake, and I’m amazed that the electrician did not ask you what the circuit would be used for.
• Next – you are not understanding the meaning of Line and Load. Line is the incoming power side of the switch. Load is the load being placed on the Line, that being the table saw motor.
• A typical 240 volt table saw motor only requires three wires, two hots,  one ground.  The size of this required circuit will be determined by the horsepower size of the motor.  Also, when changing the voltage from 120 to 240 volts, most motors require the internal wiring configuration to be changed.
• I would speculate that you have wired a direct short circuit configuration of hot to hot or a hot to neutral which is causing the circuit breaker to trip off.
• In summary, it would have been great if you would have shown the table saw to the electrician and allowed him to wire specifically, and provide the switch and motor connections.

### Electrical Wire for the Home

Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.

### Wiring 240 Volt Electrical Outlet

Home electrical wiring includes 110 volt outlets and 240 volt outlets and receptacles which are common place in every home. See how electrical outlets for the home are wired.

Electrical Outlets

### Garage Electrical Wiring

Fully Explained Photos and Wiring Diagrams for Garage Electrical Wiring with Code Requirements for most new or remodel projects.

### Work Shop Electrical Wiring

Fully Explained Photos and Wiring Diagrams for Workshop Electrical Wiring with Code Requirements for most new or remodel projects.

 » You Can Avoid Costly Mistakes! « Here's How to Do It: Wire It Right with the help of my Illustrated Wiring Book Great for any Home Wiring Project.
 Complete Guide to Home Electrical Wiring Perfect for Homeowners, Students, Handyman, Handywomen, and Electricians Includes: Wiring GFCI Outlets Wiring Home Electric Circuits 120 Volt and 240 Volt Outlet Circuits Wiring Light Switches Wiring 3-Wire and 4-Wire Electric Range Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet How to Troubleshoot and Repair Electrical Wiring Wiring Methods for Upgrading Electrical Wiring NEC Codes for Home Electrical Wiring ....and much more.

Not the answer you're looking for?

220 Volt Wiring Motor , , , , ,

Or Ask Dave a Question

 Previous Article Next Article

Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.

#### FAQs Frequently Asked Questions and Comments

5 Responses to “Converting a 120 Volt Motor to 240 Volts”
1. John Healey says:

I bought 2 ALECO DRYWALL SANDERS from a source online. They both have 120 volt electric motors. Can these motors be changed to 240 volts as I live in New Zealand where our country is 240 volts. I look forward to hearing from you.
Kind Regards,
John

• Dave Rongey says:

Hi John,
Typically the voltage of these types of motors cannot be changed unless it is specifically stated on the label. However you may want to contact the manufacturer and see if they recommend a voltage converter that may be used to change the voltage from 240 to 120.
I hope this helps you,
Dave

2. don Julien says:

I have a 700 hp 900 rpm 4999 volt electric motor (3).
It is 120 v 60HZ.
I would like to change it to 220 Volts 50HZ?
Is it possible to begin with?
Is it fairly simple(less expensive)?
Is it very time consuming(More expensive)?
How does one do it?

Much Appreciated

don julien